|MAXIMUM NET WEIGHT PER FLOOR (pounds)b|
|Floor||Unprotecteda||Protected in accordance with Section 5106.2a, c||Protected in accordance with Section 5106.3c|
For SI: 1 pound = 0.454 kg, 1 square foot = 0.0929 m2.
Level 2 and 3 aerosol containers shall not be stacked more than 6 feet (1829 mm) high from the base of the aerosol array to the top of the aerosol array unless the containers are placed on fixed shelving or otherwise secured in an approved manner. Where storage or retail display is on shelves, the height of such storage or retail display to the top of aerosol containers shall not exceed 8 feet (2438 mm).
- Display areas that use a portion of combustible cartons that consist of only the bottom panel and not more than 2 inches (51 mm) of the side panel are allowed.
- When the display area is protected in accordance with Tables 220.127.116.11(a) through 18.104.22.168(l) of NFPA 30B, storage of aerosol products in combustible cartons is allowed.
Where an automatic sprinkler system is required for the protected retail display of aerosol products, the wet-pipe automatic sprinkler system shall be in accordance with Section 903.3.1.1. The minimum system design shall be for an Ordinary Hazard Group 2 occupancy. The system shall be provided throughout the retail display area.