// CODE SNIPPET
2307.5 Additional Requirements for LP-gas Dispensers and Equipment
JUMP TO FULL CODE CHAPTER
LP-gas dispensers and related equipment shall comply with the following provisions.
- Pumps shall be fixed in place and shall be designed to allow control of the flow and to prevent leakage and accidental discharge.
- Dispensing devices installed within 10 feet (3048 mm) of where vehicle traffic occurs shall be protected against physical damage by mounting on a concrete island 6 inches (152 mm) or more in height, or shall be protected in accordance with Section 312.
- Dispensing devices shall be securely fastened to their mounting surface in accordance with the dispenser manufacturer's instructions.
Related Code Sections
2307.5 Motor Fuel-Dispensing Facilities and Repair Garages, Additional Requirements for LP-gas Dispensers and Equipment
LP-gas dispensers and related equipment shall comply with the following provisions. Pumps shall be fixed in place and shall be designed to allow ...
2017 LA City Fire Code > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2307 Liquefied Petroleum Gas Motor Fuel-Dispensing Facilities > 2307.5 Additional Requirements for LP-gas Dispensers and Equipment
Section 6106 Liquefied Petroleum Gases, Dispensing and Overfilling
by the required percentage of the water capacity marked on the container. Portable LP-gas containers shall not be refilled unless equipped ...
309.5 General Requirements, Refueling
Powered industrial trucks using liquid fuel, LP-gas or hydrogen shall be refueled outside of buildings or in areas specifically approved ...
2017 LA City Fire Code > 3 General Requirements > 309 Powered Industrial Trucks and Equipment > 309.5 Refueling
6106.3 Liquefied Petroleum Gases, Dispensing Locations
The point of transfer of LP-gas from one LP-gas container to another shall be separated from exposures as specified in NFPA 58 ...
2017 LA City Fire Code > 61 Liquefied Petroleum Gases > 6106 Dispensing and Overfilling > 6106.3 Dispensing Locations
3104.16 Tents and Other Membrane Structures, LP-gas
The storage, handling and use of LP-gas and LP-gas equipment shall be in accordance with Sections 3104.16.1 through 3104.16.3 ...
2017 LA City Fire Code > 31 Tents and Other Membrane Structures > 3104 Temporary and Permanent Tents and Membrane Structures > 3104.16 LP-gas