// CODE SNIPPET
1308.1.1 Addition to Existing System
JUMP TO FULL CODE CHAPTER
Where additional appliances are being connected to a gas piping system, the existing piping shall be checked to determine whether it has adequate capacity. Where inadequate, the existing system shall be enlarged as required, or separate gas piping of approved capacity shall be provided. [NFPA 54:5.1.2]
Related Code Sections
1308.1.1 Fuel Gas Piping, Addition to Existing System
Where additional appliances are being connected to a gas piping system, the existing piping shall be checked to determine whether it has adequate ...
Los Angeles Mechanical Code > 13 Fuel Gas Piping > 1308.0 Gas Piping System Design, Materials, and Components > 1308.1 Installation of Piping System > 1308.1.1 Addition to Existing System
3101F.3 [SLC] Marine Oil Terminals, Applicability
operations manual after adoption of this code. Addition of new structural components or systems at an existing MOT that are structurally independent ...
Los Angeles Building Code > 31F [SLC] Marine Oil Terminals > 3101F [SLC] Introduction > 3101F.3 Applicability
449.1 Special Detailed Requirements Based on Use and Occupancy, Automatic Sprinkler System
Automatic sprinkler systems shall be installed in: New facilities, including additions; Existing facilities to which a project adds the lesser ...
Los Angeles Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 449 Public Libraries [SL and SFM] > 449.1 Automatic Sprinkler System
R313.1 Building Planning, Townhouse Automatic Fire Sprinkler Systems
not be required where additions or alterations are made to existing townhouses that do not have an automatic residential fire sprinkler system ...
Los Angeles Residential Code > 3 Building Planning > R313 Automatic Fire Sprinkler Systems > R313.1 Townhouse Automatic Fire Sprinkler Systems