// CODE SNIPPET
188.8.131.52 Activation of Mechanical Ventilation and Pressurized Enclosure Systems
JUMP TO FULL CODE CHAPTER
The required mechanical system shall operate upon the activation of the smoke detectors specified in 184.108.40.206.1 and by manual controls accessible to the fire department. The required system also shall be initiated by the following, if provided:
Related Code Sections
220.127.116.11 Means of Egress, Activation of Mechanical Ventilation and Pressurized Enclosure Systems
For both mechanical ventilation and pressurized enclosure systems, the activation of the systems shall be initiated by a smoke detector installed ...
Life Safety Code 2018 of Kansas > 7 Means of Egress > 7.2 Means of Egress Components > 7.2.3 Smokeproof Enclosures > 18.104.22.168 Activation of Mechanical Ventilation and Pressurized Enclosure Systems
5307.4.4 Compressed Gases, Pressurization and Ventilation
activated by the gas detection system, the mechanical ventilation system shall remain on until manually reset. The exhaust system intakes shall ...
Fire Code 2018 of Kansas > 53 Compressed Gases > 5307 Compressed Gases Not Otherwise Regulated > 5307.4 Carbon Dioxide Enrichment Systems > 5307.4.4 Pressurization and Ventilation
5003.8.5.2 Hazardous Materials—General Provisions, Ventilation
Exhausted enclosures shall be provided with an exhaust ventilation system. The ventilation system for exhausted enclosures shall be designed ...
Fire Code 2018 of Kansas > 50 Hazardous Materials—General Provisions > 5003 General Requirements > 5003.8 Construction Requirements > 5003.8.5 Exhausted Enclosures > 5003.8.5.2 Ventilation
909.20.4 Fire Protection and Life Safety Systems, Mechanical Ventilation Alternative
The provisions of Sections 909.20.4.1 through 909.20.4.4 shall apply to ventilation of smokeproof enclosures by mechanical means ...
Building Code 2018 of Kansas > 9 Fire Protection and Life Safety Systems > 909 Smoke Control Systems > 909.20 Smokeproof Enclosures > 909.20.4 Mechanical Ventilation Alternative
22.214.171.124 Means of Egress, Mechanical Ventilation
Smokeproof enclosures using mechanical ventilation shall comply with 126.96.36.199 and the requirements of 188.8.131.52.1 through 184.108.40.206.4 ...
Life Safety Code 2018 of Kansas > 7 Means of Egress > 7.2 Means of Egress Components > 7.2.3 Smokeproof Enclosures > 220.127.116.11 Mechanical Ventilation