// CODE SNIPPET
1127A.2.4 Accessible Urinals
JUMP TO FULL CODE CHAPTER
When urinals are provided, at least one shall comply with the following:
- Height and wall projection. Urinals shall be floor mounted (stall type) or wall hung. The rim of the wall hung urinals shall be 17 inches (432 mm) maximum above the finish floor. Urinals (floor mounted and wall hung) shall be131/2 inches (343 mm) deep minimum measured from the outer face of the rim to the back of the fixture.
- Flush controls. Flush controls shall be hand operated or automatic. Hand operated controls shall be operable with one hand, shall not require tight grasping, pinching or twisting of the wrist and shall be mounted no more than 44 inches (1118 mm) above the floor. The force required to activate controls shall be no greater than 5 pounds (22.2 N). Electronic automatic flushing controls are preferable.
- Clear floor space. A clear floor space 30 inches by 48 inches (762 mm by 1219 mm) shall be provided in front of the urinal to allow forward approach. The clear floor space shall comply with Section 1138A.1.4.