// CODE SNIPPET
§27-2033 Access to Boiler Room
JUMP TO FULL CODE CHAPTER
a. The owner of every multiple dwelling shall have the area, where the building's heating system is located, readily accessible to members of the department to make inspection pursuant to this chapter. In the event such area is kept under lock, a key shall be kept on the premises at all times with such person as the owner shall designate; however, if there is a person residing on the premises who performs janitorial services, such person shall hold the key. The owner shall post a notice in a form approved by the department naming such designated person and his or her location.
b. Multiple dwellings owned and operated by the New York city housing authority shall be exempt from the requirements of this section.
Related Code Sections
1004.6 Boilers, Water Heaters and Pressure Vessels, Boiler Rooms and Enclosures
Boiler rooms and enclosures and access thereto shall comply with the New York City Building Code and Chapter 3 of this code. Boiler rooms shall ...
NYC Mechanical Code 2008 > 10 Boilers, Water Heaters and Pressure Vessels > 1004 Boilers > 1004.6 Boiler Rooms and Enclosures
1004.2 Boilers, Water Heaters and Pressure Vessels, Installation
of a permanent type shall be located in the boiler room and readily accessible. Boilers shall have all controls set, adjusted and tested ...
NYC Mechanical Code 2014 > 10 Boilers, Water Heaters and Pressure Vessels > 1004 Boilers > 1004.2 Installation
1014.3 Means of Egress, Boiler, Furnace and Incinerator Rooms
Two exit access doorways are required in boiler, furnace and incinerator rooms where the area is over 500 square feet (46 m 2 ) and any fuel-fired ...
NYC Building Code 2008 > 10 Means of Egress > 1014 Exit and Exit Access Doorways > 1014.3 Boiler, Furnace and Incinerator Rooms
1015.3 Means of Egress, Boiler, Incinerator and Furnace Rooms
Two exit access doorways are required in boiler, incinerator and furnace rooms where the area is over 500 square feet (46 m 2 ) and any fuel-fired ...
NYC Building Code 2014 > 10 Means of Egress > 1015 Exit and Exit Access Doorways > 1015.3 Boiler, Incinerator and Furnace Rooms
308.4 General Regulations, Central-Heating Boilers and Furnaces
Central-heating furnaces and low-pressure boilers installed in rooms large in comparison ...
NYC Fuel Gas Code 2008 > 3 General Regulations > 308 Clearance Reduction > 308.4 Central-Heating Boilers and Furnaces