// CODE SNIPPET
[F] 909.18 Acceptance Testing
JUMP TO FULL CODE CHAPTER
Devices, equipment, components and sequences shall be individually tested. These tests, in addition to those required by other provisions of this code, shall consist of determination of function, sequence and, where applicable, capacity of their installed condition.
Smoke or fire detectors that are a part of a smoke control system shall be tested in accordance with Chapter 9 in their installed condition. Where applicable, this testing shall include verification of airflow in both minimum and maximum conditions.
Ducts that are part of a smoke control system shall be traversed using generally accepted practices to determine actual air quantities.
Dampers shall be tested for function in their installed condition.
Inlets and outlets shall be read using generally accepted practices to determine air quantities.
Fans shall be examined for correct rotation. Measurements of voltage, amperage, revolutions per minute (rpm) and belt tension shall be made.
Each smoke zone equipped with an automatic-initiation device shall be put into operation by the actuation of one such device. Each additional device within the zone shall be verified to cause the same sequence without requiring the operation of fan motors in order to prevent damage. Control sequences shall be verified throughout the system, including verification of override from the fire fighter's control panel and simulation of standby power conditions.
Testing shall be conducted in accordance with the following:
- During erection of ductwork and prior to concealment for the purposes of leakage testing and recording of device location.
- Prior to occupancy and after sufficient completion for the purposes of pressure-difference testing, flow measurements, and detection and control verification.
Approved agencies for smoke control testing shall have expertise in fire protection engineering, mechanical engineering and certification as air balancers.
A complete report of testing shall be prepared by the approved agency. The report shall include identification of all devices by manufacturer, nameplate data, design values, measured values and identification tag or mark. The report shall be reviewed by the responsible registered design professional and, when satisfied that the design intent has been achieved, the responsible registered design professional shall sign, seal and date the report.
A copy of the final report shall be filed with the fire code official and an identical copy shall be maintained in an approved location at the building.
Charts, drawings and other documents identifying and locating each component of the smoke control system, and describing its proper function and maintenance requirements, shall be maintained on file at the building as an attachment to the report required by Section 909.18.8.3. Devices shall have an approved identifying tag or mark on them consistent with the other required documentation and shall be dated indicating the last time they were successfully tested and by whom.
Related Code Sections
(6) Wiring and Protection, Acceptance Tests
Complete acceptance tests shall be performed, after the substation installation is completed, on all assemblies, equipment, conductors, and control ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 225 Outside Branch Circuits and Feeders > 225.56 Inspections and Tests > (A) Pre-Energization and Operating Tests > (6) Acceptance Tests
901.5 Fire Protection and Life Safety Systems, Acceptance Tests
Fire protection systems shall be tested in accordance with the requirements of this code and the International Fire Code . Where required ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 901 General > 901.5 Acceptance Tests
909.18 Fire Protection and Life Safety Systems, Acceptance Testing
Devices, equipment, components and sequences shall be individually tested. These tests, in addition to those required by other provisions ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 909 Smoke Control Systems > 909.18 Acceptance Testing
913.5 Fire Protection and Life Safety Systems, Acceptance Test
Acceptance testing shall be done in accordance with the requirements of NFPA 20 ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 913 Fire Pumps > 913.5 Acceptance Test
907.7 Fire Protection and Life Safety Systems, Acceptance Tests and Completion
Upon completion of the installation, the fire alarm system and all fire alarm components shall be tested in accordance with NFPA 72 ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.7 Acceptance Tests and Completion