// CODE SNIPPET
625.60 AC Receptacle Outlets Used for EVPE
JUMP TO FULL CODE CHAPTER
Electric vehicles provided with receptacle outlets for power export shall be provided with overcurrent protection integral to the power export system. The overcurrent protection shall have a nominal rating sufficient for the receptacle it protects. The overcurrent protection shall also be sufficiently rated for the maximum available fault current at the receptacle and shall be included in the interactive equipment evaluation. See 625.48.
Ground-fault circuit-interrupter protection for personnel shall be provided for all receptacles. The ground-fault circuit-interrupter indication and reset shall be installed in a readily accessible location.
Informational Note: There are various methods available to achieve ground-fault circuit-interrupter protection.
Related Code Sections
625.60 Special Equipment, AC Receptacle Outlets Used for EVPE
AC receptacles installed in electric vehicles and intended to allow for connection of off-board utilization equipment shall comply with 625.60(A ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 625 Electric Vehicle Power Transfer System > 625.60 AC Receptacle Outlets Used for EVPE
646.12 Special Equipment, Receptacles
At least one 125-volt ac, 15- or 20-ampererated duplex convenience outlet shall be provided in each work area of the MDC to facilitate the powering ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 646 Modular Data Centers > 646.12 Receptacles
(A) Special Occupancies, Receptacle Outlets
are involved, an assured equipment grounding conductor program as specified in 590.6(B)(2) shall be permitted for only those receptacle outlets used to supply ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 590 Temporary Installations > 590.6 Ground-Fault Protection for Personnel > (A) Receptacle Outlets
530.21 Special Occupancies, Plugs and Receptacles
and receptacles shall not be less than the nominal circuit voltage. Plug and receptacle ampere ratings for ac circuits shall not be less than the feeder or branch ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 530 Motion Picture and Television Studios and Similar Locations > 530.21 Plugs and Receptacles