// CODE SNIPPET
3.3.268.1 Aboveground Storage Tank.
Related Code Sections
126.96.36.199* Refueling, Aboveground Storage Tanks
Except as modified by the provisions of this subsection, aboveground storage tanks shall meet all applicable requirements of Chapters 21 and 22 ...
Fire Code 2018 of West Virginia > 42 Refueling > 42.3 Storage of Liquids > 42.3.3 Storage of Liquids > 188.8.131.52* Aboveground Storage Tanks
3.3.268.1 Definitions, Aboveground Storage Tank
A horizontal or vertical tank that is listed and intended for fixed installation, without backfill, above or below grade and is used within the scope ...
Fire Code 2018 of West Virginia > 3 Definitions > 3.3 General Definitions > 3.3.268 Tank > 3.3.268.1 Aboveground Storage Tank
184.108.40.206.1* Flammable and Combustible Liquids, Closure of Aboveground Storage Tanks
Aboveground tanks taken out of service or abandoned shall be emptied of liquid, rendered vapor-free, and safeguarded against trespassing ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.21 Storage of Liquids in Tanks — Requirements for All Storage Tanks > 66.21.7 Operation of Storage Tanks > 220.127.116.11 Removal From Service of Storage Tanks > 18.104.22.168.1* Closure of Aboveground Storage Tanks
66.22.4* Flammable and Combustible Liquids, Location of Aboveground Storage Tanks
22.214.171.124.3 and Table 126.96.36.199.1(b). [ 30: 188.8.131.52] Table 184.108.40.206.3 Location of Aboveground Storage Tanks Storing Stable Liquids — Internal ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.22 Storage of Liquids in Tanks — Aboveground Storage Tanks > 66.22.4* Location of Aboveground Storage Tanks