// CODE SNIPPET
5704.2.9.5 Above-Ground Tanks Inside of Buildings
JUMP TO FULL CODE CHAPTER
Above-ground tanks storing Class I, II and IIIA liquids inside buildings shall be equipped with a device or other means to prevent overflow into the building including, but not limited to: a float valve; a preset meter on the fill line; a valve actuated by the weight of the tank's contents; a low-head pump that is incapable of producing overflow; or a liquid-tight overflow pipe not less than one pipe size larger than the fill pipe and discharging by gravity back to the outside source of liquid or to an approved location. Tanks containing Class IIIB liquids and connected to fuel-burning equipment shall be provided with a means to prevent overflow into buildings in accordance with Section 5704.2.7.5.8.
Related Code Sections
5704.2.9.5 Flammable and Combustible Liquids, Above-Ground Tanks Inside of Buildings
Above-ground tanks inside of buildings shall comply with Sections 5704.2.9.5.1 and 5704.2.9.5.2 ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.9 Above-Ground Tanks > 5704.2.9.5 Above-Ground Tanks Inside of Buildings
2306.2.2 Motor Fuel-Dispensing Facilities and Repair Garages, Above-Ground Tanks Located Inside Buildings
Above-ground tanks for the storage of Class I, II and IIIA liquid fuels are allowed to be located in buildings. Such tanks shall be located ...
Fire Code 2018 of Kansas > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2306 Flammable and Combustible Liquid Motor Fuel-Dispensing Facilities > 2306.2 Method of Storage > 2306.2.2 Above-Ground Tanks Located Inside Buildings
M2201.2 Special Piping and Storage Systems, Above-Ground Tanks
The maximum amount of fuel oil stored above ground or inside of a building shall be 660 gallons (2498 L). The supply tank shall be supported on rigid ...
Residential Code 2018 of Kansas > 22 Special Piping and Storage Systems > M2201 Oil Tanks > M2201.2 Above-Ground Tanks
1307.1 Fuel Oil Piping and Storage, Building Shutoff
A shutoff valve shall be installed on the fuel-oil supply line at the entrance to the building. Inside or above-ground tanks are permitted to have ...
Mechanical Code 2018 of Kansas > 13 Fuel Oil Piping and Storage > 1307 Fuel Oil Valves > 1307.1 Building Shutoff
5704.2.7.4 Flammable and Combustible Liquids, Emergency Venting
Stationary, above-ground tanks shall be equipped with additional venting that will relieve excessive internal pressure caused by exposure to fires ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.7 Design, Fabrication and Construction Requirements for Tanks > 5704.2.7.4 Emergency Venting