// CODE SNIPPET
802.3.6 Above-Ceiling or Nonducted Air Handling System
JUMP TO FULL CODE CHAPTER
Where a venting system passes through an above-ceiling air space or other nonducted portion of an air-handling system, it shall conform to one of the following requirements:
- The venting system shall be a listed special gas vent, other system serving a Category III or Category IV appliance, or other positive pressure vent, with joints sealed in accordance with the appliance or vent manufacturer's instructions.
- The vent system shall be installed such that no fittings or joints between sections are installed in the above-ceiling space.
- The venting system shall be installed in a conduit or enclosure with joints between the interior of the enclosure and the ceiling space sealed. [NFPA 54:188.8.131.52]