// CODE SNIPPET
Section P-606 Abandoned Piping
JUMP TO FULL CODE CHAPTER
Abandoned water service shall be capped or plugged at the curb or shall have the ferrule removed. Abandoned water piping within the building shall be capped or plugged with a fitting.
Related Code Sections
Section P-606 Pipe Supports, Abandoned Piping
Abandoned laterals shall have the house trap removed, and the pipe shall be hermetically sealed by a cap or plug at the curb line. Abandoned drainage ...
5704.2.14.1 Flammable and Combustible Liquids, Removal
the ground. Exception: Piping is allowed to be abandoned in place where the fire code official determines that removal is not practical. Abandoned ...
2018 Philadelphia Fire Code > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.14 Removal and Disposal of Tanks > 5704.2.14.1 Removal
M2201.7 Special Piping and Storage Systems, Tanks Abandoned or Removed
Exterior above-grade fill piping shall be removed when tanks are abandoned or removed. Tank abandonment and removal shall be in accordance ...
2018 Philadelphia Residential Code > 22 Special Piping and Storage Systems > M2201 Oil Tanks > M2201.7 Tanks Abandoned or Removed
1301.5 Fuel Oil Piping and Storage, Tanks Abandoned or Removed
All exterior above-grade fill piping shall be removed when tanks are abandoned or removed. Tank abandonment and removal shall be in accordance ...
2018 Philadelphia Mechanical Code > 13 Fuel Oil Piping and Storage > 1301 General > 1301.5 Tanks Abandoned or Removed
P2910.12 Water Supply and Distribution, System Abandonment
maintain such system, the system shall be abandoned and shall comply with the following: System piping connecting to a utility-provided water system ...
2018 Philadelphia Residential Code > 29 Water Supply and Distribution > P2910 Nonpotable Water Systems > P2910.12 System Abandonment