// CODE SNIPPET
(4) 50/60 HZ Motors
JUMP TO FULL CODE CHAPTER
Motors with 50-and 60-Hz ratings shall be marked with a code letter designating the locked-rotor kilovolt-ampere (kVA) per horsepower (hp) on 60 Hz.
Related Code Sections
(4) Equipment for General Use, 50/60 HZ Motors
Motors with 50-and 60-Hz ratings shall be marked with a code letter designating the locked-rotor kilovolt-ampere (kVA) per horsepower (hp) on 60 Hz ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.7 Marking on Motors and Multimotor Equipment > (B) Locked-Rotor Indicating Code Letters > (4) 50/60 HZ Motors
22.214.171.124.1 Electric Elevators,
a voltage reduction of 30% of the nominal input voltage for 0.5 cycles at 60 Hz and a voltage reduction of 60% of nominal input voltage for 5 cycles ...
Safety Code for Elevators and Escalators 2016 of Minnesota > 2 Electric Elevators > 2.26 Operating Devices and Control Equipment > 2.26.4 Electrical Equipment and Wiring > 126.96.36.199 > 188.8.131.52.1
184.108.40.206.6 General Requirements, Insulation Test
The insulation of the electrical parts shall withstand a test with a root-mean square (effective) voltage of twice the rated voltage plus 1 000 V, 60 ...
Safety Code for Elevators and Escalators 2016 of Minnesota > 8 General Requirements > 8.3 Engineering Tests, Type Tests, and Certification > 8.3.3 Type Tests of Interlocks, Combination Mechanical Locks and Electric Contacts, and Door or Gate Electric Contacts > 220.127.116.11 Required Tests and Procedure > 18.104.22.168.6 Insulation Test
(B) Special Equipment, Groups of Welders
setting used. The duty cycle is the percentage of the time during which the welder is loaded. For instance, a spot welder supplied by a 60-Hz ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 630 Electric Welders > 630.31 Ampacity of Supply Conductors > (B) Groups of Welders
(B) Wiring and Protection, Through Spark Gap or Device
gap for a listed device shall have a 60-Hz breakdown voltage of at least twice the primary circuit voltage but not necessarily more than 10 kV ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 242 Overvoltage Protection > 242.54 Interconnections > (B) Through Spark Gap or Device