// CODE SNIPPET
(2) 16 AWG Copper
JUMP TO FULL CODE CHAPTER
10 amperes, provided all the following conditions are met:
- Continuous loads do not exceed 8 amperes.
- Overcurrent protection is provided by one of the following:
Related Code Sections
(2) Wiring and Protection, 16 AWG Copper
of the following: Branch-circuit-rated circuit breakers listed and marked for use with 16 AWG copper wire Branch-circuit-rated fuses listed ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.4 Protection of Conductors > (D) Small Conductors > (2) 16 AWG Copper
(2) Equipment for General Use, 16 AWG Copper
16 AWG individual copper conductors installed in a cabinet or enclosure, copper conductors that are part of a jacketed multiconductor cable assembly ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.22 Single Motor > (G) Conductors for Small Motors > (2) 16 AWG Copper
(C) Wiring Methods and Materials, Class 1 Circuit Conductors
Insulated conductors of 18 AWG and 16 AWG copper shall also be in accordance with 725.49 ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 336 Power and Control Tray Cable: Type TC > 336.104 Conductors > (C) Class 1 Circuit Conductors
522.22 Special Occupancies, Conductor Ampacity
Ampacities for conductors sized 16 AWG and smaller shall be as specified in Table 522.22. Table 522.22 Conductor Ampacity Based on Copper ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 522 Control Systems for Permanent Amusement Attractions > 522.22 Conductor Ampacity
760.49 Special Conditions, NPLFA Circuit Conductors
Only copper conductors shall be permitted to be used for fire alarm systems. Size 18 AWG and 16 AWG conductors shall be permitted to be used ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 760 Fire Alarm Systems > 760.49 NPLFA Circuit Conductors